After starting up engine in high-speed rail, inverter will restart
BP Series Pure Sine Wave Inverter 300W 110VDC 220VAC
1. When used in trains, the inverter can be started up normally after opening its front-end circuit breaker;
2. After starting up internal combustion engine in train, inverter display will restart if supply power to inverter;
3. The inverter works normally after restart.
Analysis of the possibility of the cause
1. Products like electric generator, their output voltage amplitude is large after starting up;
2. 110V inverter's input voltage ranges from 85V to 135V;
3. Analysis shows the reason of display restart is the output voltage fluctuation exceeds rated voltage range.
Solutions and steps
1. Do not connect inverter to electric generator's output interface directly, the inverter runs better if connected to battery with steady output;
2. Add a regulated power supply between generator and inverter.
BPlus-3000W inverter will restart when it loaded with 1.6KW
Model BPlus Series Pure Sine Wave Inverter 3000W Description When BPlus-3000W is loaded with 1.6KW, it will restart in about 4 minutes. Analysis of the possibility of the cause After inspection, it is found that the user uses a low-quality DC circuit ...
No output after running 2-3 months of BP 2000 watt power inverter
Model BP series pure sine wave inverter 2000W 12VDC 220VAC Description No output after using for 2-3 months, red and blue light are on at same time. Analysis of the possibility of the cause 1.The ambient temperature and humidity of the inverter is ...
600W inverter beeps continuously but input and output voltages are normal
Model BP Series Pure Sine Wave Inverter 12VDC 220VAC 600W Description 1. After starting up, the buzzer will beep for a long time, the output end of the bulb can be lighted normally, the working indicator is always on, and the fault indicator is not ...
Helios II Series Power Inverter's capacitance bulged or exploded
Model Helios II Series off grid solar inverter Description If the input voltage of battery exceeded defult value, capacitance will bulge/explode and further damage DC input part MOS tube. Fault Causes The input voltage of DC battery was too high. ...
1000W inverter stop working suddenly and can't restart
Model BP Series Pure Sine Wave Inverter 12VDC 220VAC 1000W Description The inverter suddenly stop working under normal power-on conditions, and then can’t restart. Analysis of the possibility of the cause 1. Check the main board and find that the ...